GUARD air curtains are designed to protect against heat loss in medium and large objects with a required maximum mounting height of up to 4m, especially for example: supermarkets, large commercial premises, repair shops, car repair shops, sports halls and exhibition areas.
Air curtains technical details
|Parameter / enter the e-shop||Guard 100W||Guard 150W||Guard 200W|
|Price list, Eur||664||803||939|
|Module length [m]||1||1,5||2|
|Maximum door weight [m]||4||4||4|
|Maximum air flow [m3/h]||1 200 / 1 550 / 2 000||2 200 / 3 000 / 3 600||2 900 / 4 000 / 4 800|
|Heating power [kW]||10 - 16 ||20 - 29||25 - 40|
|Temperature increase ΔT [C]*|| || || |
|Maximum operating pressure [MPa]||1,6||1,6||1,6|
|Connection, diameter ["]||1/2||1/2||1/2|
|rated motor voltage, consumption [V / Hz A]||230 / 50 1,4A||230 / 50 1,8A||230 / 50 2,4A|
|Motor current [W]||37 / 80 / 160 ||51 / 106 / 220 ||75 / 162 / 320 |
|Electric heater, rated voltage, consumption [V / Hz A]**|| || || |
|Weight with water / without water [kg]||18,0 / 16,5||22,6 / 20,5||31,0 / 28,0|
|Noise level - operation I / II / III [dB (A)]||44 / 49 / 59||45 / 49 / 61||46 / 49 / 61|
|IP coverage||IP 21||IP 21||IP 21|
* temperature increase for 18 °C ambient air
** energy consumption at an ambient air temperature of 18 °C and a cable length of 10 m
Energy consumption [A] increases with lower inlet air temperature or longer supply cables.
Air curtains - heating performance
A new type of PTC heating element is used in GUARD curtains with electric heating. It is a modern and safe solution, characterized by the following features:
- heating element without voltage,
- lower temperature of the heating body than in the old type (e.g. heating coil),
- large heat exchange surface (contact area of the exchanger with the heated air),
- automatic power adjustment depending on the air flow,
- elimination of the risk of overheating - self-cooling heating module (when air flow is reduced),
- low energy demand.
Dimensions of air curtains
Installation of air curtains
When determining the installation location of the curtain, it is necessary to take into account, in particular, suitability in terms of access for maintenance. Installation is possible
- horizontal, under the ceiling using mounting pins,
- on the wall using a horizontal holder,
- vertical using mounting brackets.
Control of air curtains
Control of the air curtain is realized using the Panel COMFORT controller, which allows the adjustment of the air flow. The control panel is placed outside the air flow zone. A maximum of 2 GUARD modules can be connected to one Panel COMFORT. Part of the air curtain is the GUARD (DC) door switch, it is an accessory for switching the curtain on and off depending on the opening of the door. It is intended for internal installation.